There is a wide variety of refrigerants used in air conditioning equipment depending on the application.
In general the most common refrigerants used in the industry belong to the following three categories -
There is extensive research going on to identify new refrigerants that can be used to replace the CFC
- CFC - These are the Chloro Fluoro Carbon refrigerants, such as R11, R12, R113, R114, etc. These
refrigerants were identified as the most harmful to Ozone layer by the Montreal Protocol, and
were phased out in 2000. However they are still being used in the older machines, with
precautions to minimize release in accordance with EPA regulations. The most common application
of these refrigerant is in the large centrifugal chillers. R12 was also used commonly in the older
cars for air condition.
- HCFC - These are the Hydro Chloro Fluoro Carbon refrigerants, such as R22, R123, etc. These
refrigerants were identified as slightly harmful to the Ozone layer by Montreal Protocol, and will
be completely phased out by 2030. See the EPA link below for the different stages of the
phaseout. The R22 refrigerant is commonly used in reciprocating type of compressors, while R123
is used in centrifugal chillers as a temporary replacement for R11.
- HFC - These are the Hydro Fluoro Carbon refrigerants, such as R134a. These are the new
refrigerants that do not harm the Ozone layer, and are being used in the newer machines to
replace the CFC and HCFC. R134a is now commonly used as a replacement of R12 and R500, and in
all new cars air conditioning systems. R407c is used as a replacement for R22. One of the other
common HFC used in new equipment now is R410a.
and HCFC refrigerants. Currently R134a is the most commonly used new refrigerant. The various
refrigerants have different characteristics, which make them suitable for a particular application.
Following link provides more useful information on EPA regulations for refrigerants -
Refrigerant Analysis for Optimum Performance
Information on the test analysis required for optimum performance of various refrigerants is provided
under the Membership Resources button below. This provides the typical contaminants to look for and
their limits to prevent any damage to the equipment and provide optimum performance. In case you are
not a member, please click on the Membership button below to see how you can become a member,
and a summary of all the various resources available to you as a member.